Flashing LED on Electricity Meter
Flashing LED On Electricity Meter
Find out how to interpret the flashing LED light on electronic electricity meterseducation | general | solar
If you have had an electricity meter
installed in the last few years, and certainly if you taken advantage of the feed in tariff to have a solar PV
installation, your electricity meter(s) will be electronic with an LED which flashes. The rate of this flashing is proportional to the amount of power
passing through the meter, and so useful information is there to be collected.
Pictured above as an example is an A100C
single phase kWh meter which is commonly installed in the UK. To the right hand side of the meter reading is a small LED together with some writing as pictured below:
This type of meter will always be labelled in this way with a certain number of Imp/kWh
. Imp/kWh is short for Impressions per kWh (unit) of electricity which passes through the meter where one 'impression' is a brief flash of an LED.
The majority of meters are labelled 1000 Imp/kWh which means that the LED will flash 1000 times for each kWh of electricty which passes through. The rate of the flashing of the LED tells you how much power is currently passing through the meter.
For the meter in the photographs above, the label states 1000 Imp/kWh
, so the LED will flash 1000 times per unit of electricity. We can use that value of 1000 to estimate the power. If a constant 1000W (1kW) is going through the meter, then in one hour (3600 seconds) the LED will flash 1000 times, so the LED will flash once every 3600/1000 = 3.6 seconds. With a constant 3000W (3kW) going through the meter, in one hour 3 kWh will pass through the meter (3 x 1000 = 3000 flashes in 3600 seconds) so the LED will flash every 3600 / 3000 = 1.2 seconds.
It is more likely that you will want to measure the rate of flashing, and from that calculate the power going through the meter. This can easily be achieved by reversing the calculation above as follows:
(kW) = 3600
(secs in 1hr) divided by (the seconds between flashes * number of Imp/kWh printed on meter)
For example, if the LED flashes once every 5.2 seconds on a meter labelled 800 kWh, the power going through the meter at that time will be 3600 / (5.2 * 800) = 0.865 kW.
(To measure the number of seconds between flashes it is best to start timing on a flash, and then time how long for 10 more flashes. Divide that time by 10 to get the average number of seconds per flash. Obviously this only works if the power is constant - if someone turns on the kettle half way through your time measurement the results will not be valid.)
Article Last Modified: 11:27, 17th May 2012
Comment on this Article
If you have any comments on this article, please email them to firstname.lastname@example.org
Recommended Related Articles
People who read this article also enjoyed the following articles:Low Voltage Battery Disconnect Circuits
Find out more about low voltage battery disconnect (LVD) circuits - used to protect batteriesArticle Last Modified: 12:47, 31st Mar 2012electric circuit | electronics | storage12 Volt Battery Monitor Circuit with LM3914
Accurately monitor battery voltage with LM3914 LED bar graph driverArticle Last Modified: 13:09, 4th Aug 2012storage | electric circuit | educationRelays and Renewable Energy
Find out more about relays and their uses in renewable energy applicationsArticle Last Modified: 13:33, 14th Aug 2010electric circuit | electronics | generalSolar Tracker
Set up solar panels to track the motion of the sun across the sky to maximise power outputArticle Last Modified: 10:46, 27th Jan 2012solar | electronicsSolar Charge Controllers on eBay
Find out about the selection of solar charge controllers available on ebayArticle Last Modified: 15:43, 29th Jul 2008solar | electronics | shoppingHow Do PV Solar Panels Work
Find out how photovoltaic solar cells generate electricityArticle Last Modified: 14:04, 18th Jul 2011solar | educationSolar Charge Controller
Find out more about Solar Charge ControllersArticle Last Modified: 11:12, 29th Oct 2009solar | electronics | electric circuitDual Powered Lighting Circuit
Power a lighting circuit from renewable energy or mains electricityArticle Last Modified: 08:18, 14th Nov 2007lighting | electric circuit